>> Contact Information
GREEGOO Electric Co.,Ltd.
No.6 Floor,Jinye Mansion, Lvzhuang, Liushi, Yueqing, Zhejiang, 325604 P.R. China
Mob: +86-159 5877 6000
Fax: +86-4008875666 Ext 088150
Visit us on the web at...
Magnetic Contactors (CJX7 A)
CJX7-9~110 AC contactor (hereafter refer to as contactor) is mainly used in power system with AC 50Hz (or 60Hz), therated working voltage up to 660V, under the appplication category of AC-3, when the rated working voltage 380V, the rated operating current to 110A electrical, for the long-distance range making and breaking the electric circuit, and combines the electromagnetism starter with the suitable thermal overload relay or the electronic protector to protect against the possible overload electric circuit during operation(running).
Type and meaning
1: A.C contact
2: Design code
3: The basic specification code is indicated with the rated working voltage
380V rated operating current numerical value under AC-3 application category
4: The main contact pair indicatedˇˇwith two figures, ones placeˇˇexpressed NC contact Pair;
The tens digit expressed NO contact pair;
5: The auxiliary contact pair indicated with two figures, ones placeexpressed NC;
The contact pair, the tens digit expressed NO contact pair;
Normal Working Condition and Mounting condition
■ The installation site elevation does not surpass 2000m;
■ Ambient air temperature should not over +40℃, also not over +35℃ within 24h, the lower limit of ambient air
temperature is -5℃;
■ The air relative humidity at installation site should not over 50% when the maximum temperature is +40℃;the higher
relative humidity are allowed under lower temperature, foir example, 90% at 20℃ .It must take the measures on on
the product occuring dew because of the change of temperature.
■ The installation site pollution chass is 3;
■ The contactor can be mounted vertically or horizontally. If vertically mounts, the gradient between the mounter surface
and the perpendicular plane is not bigger than +30%; (See Fig1).
■ The allowable application category of main circuit and the auxiliary circuit of the contactor and it’s code see Table 1 application category of main circuit and the auxiliary circuit of the contactor and it’s code
|Circuit||Application category code||Example of the typical usage|
|Main circuit||AC-1||Noninductive or the micro ineuductive load, resistance furnace|
|AC-2||The starting and breaking of wire winding type asynchronous motor|
|AC-3||The starting and breaking during operation of cage asynchronous motor|
|AC-4||The starting,plug braking or reverse revolution,spot moving of cage asynchronous motor|
|Auxliary circuit||AC-15||Control AC electromagnet load (>72VA)|
|DC-13||Control DC magnet load|
■ Contactor reated insulation voltage (Ui), rated working voltage (Ue), conventional free air heat current (lth), rated operating current (le)and rated work rate see Table 2.
air heat current ith
|AC-3 rated operating current Ie A||Control the max.power KW of generator|
If you would like a quotation or further information on this product, please fill in the form below and we will reply to you within 1 working day.
Copyright 2013 © GREEGOO Electric Co.,Ltd. All Rights Reserved. E-mail:Peter@greegoo.com
Add: No.6 Floor,Jinye Mansion, Lvzhuang, Liushi, Yueqing, Zhejiang, 325604 P.R. China Tel: +86-577-62776000 Mob: +86-159 5877 6000 Fax: +86-4008875666 Ext 088150